九洲国际

九洲国际·(集团)有限公司官网
九洲国际·(集团)有限公司官网
您的位置:首页 > 产品中心 > CE认证电缆
九洲国际·(集团)有限公司官网
CE认证电缆

H05VVD3H6-F (0.75mm2-1mm2 3-24 芯,,,,,25-60 芯)

  • 产品简介: H05VVD3H6-F  Application Scope:Suitable for traveling inside the elevator free-hanging suspended over 80 meters in length, and moving speed no more than 4 m / s , cable can also be used as a travel lift and cable reel cableH05VVD3H6-F Structure:Conductor: stranded bare copper or tinned copper comply with VDE 0295 CLASS 5 & CLASS 6, IEC 228Insulation: PVC / TI2 PVC comply with DIN VDE 0281.Color ID: in line with standard HD 308Reinforcement:Galvanized steel wireSheath material: PVC / TM2 PVCApplication Standard:HD21, VDE 0281, EN 50214-2006H05VVD3H6-F Characteristics and Compliance:Features: excellent resistance to ?ex;good oil resistance, cold resistance, moisture resistance excellent wear resistance, withstand greater mechanical stressConformity Approval: ROHS CEH05VVD3H6-F Technical Parameters:Rated Voltage: 300/500V Test Voltage: insulation thickness ≤ 0.6: 1500V,Final test: 2000VMin. Bending RadiusCable laying installation allows bending radius should be not less than 6 times the cable small side.Temperature Range: -15 To +70 ℃?ame test: VDE0472 804 part by Class B Experimental and IEC332-1
  • 配套服务:
    支持定制 物流配送 免费装置 现场培训 后期维护
  • 相关产品:

产品介绍

H05VVD3H6-F  Application Scope:

Suitable for traveling inside the elevator free-hanging suspended over 80 meters in length, and moving speed no more than 4 m / s , cable can also be used as a travel lift and cable reel cable


H05VVD3H6-F Structure:

Conductor: stranded bare copper or tinned copper comply with VDE 0295 CLASS 5 & CLASS 6, IEC 228

Insulation: PVC / TI2 PVC comply with DIN VDE 0281.

Color ID: in line with standard HD 308

Reinforcement:Galvanized steel wire

Sheath material: PVC / TM2 PVC

Application Standard:HD21, VDE 0281, EN 50214-2006


H05VVD3H6-F Characteristics and Compliance:

Features: excellent resistance to ?ex;

good oil resistance, cold resistance, moisture resistance excellent wear resistance, withstand greater mechanical stress

Conformity Approval: ROHS CE


H05VVD3H6-F Technical Parameters:

Rated Voltage: 300/500V 

Test Voltage: insulation thickness ≤ 0.6: 1500V,

Final test: 2000V

Min. Bending Radius

Cable laying installation allows bending radius should be not less than 6 times the cable small side.

Temperature Range: -15 To +70 ℃

?ame test: VDE0472 804 part by Class B Experimental and IEC332-1

企业优势

  • 九洲国际·(集团)有限公司官网

    多年行业生产履历

    本公司是集研发、制造和销售于一体的综合性环保企业。。从业多年,,,,,拥有富厚的履历。。
  • 九洲国际·(集团)有限公司官网

    产品种类多,,,,,规格全

    产品远销海内外各个省市和地区。。在海内行业中享有很高的信誉和着名度
  • 九洲国际·(集团)有限公司官网

    品质过硬,,,,,价钱优惠

    设有严酷的质检工序,,,,,包管产品的品质及格,,,,,源头厂家直销,,,,,价钱更优惠
  • 九洲国际·(集团)有限公司官网

    优异团队,,,,,实力过硬

    公司拥有一批具有富厚履历的工程手艺职员,,,,,具有自主研发设计生产的能力

PRODUCT

产品中心

PRODUCT CENTER

Contact

联系九洲国际

Contact Us

联系人:曹司理

固话:021-37100188

电话:16621098610

邮箱:

地点:上海市奉贤区浦卫公路875号

16621098610
code
【网站地图】
H05VVD3H6-F (0.75mm2-1mm2 3-24